How do you test a 3 phase motor for insulation?
- Disconnect the motor from power supply using main breaker.
- Use do not operate tag to avoid injury.
- Open the motor terminal box.
- Check for current using the tester/Ground motor terminals / short motor terminals for safety purpose to avoid getting shock.
What is the acceptable Megger reading for a motor?
The rule may be stated: Insulation resistance should be approximately one megohm for each 1,000 volts of operating voltage, with a minimum value of one megohm. For example, a motor rated at 2,400 volts should have a minimum insulation resistance of 2.4 megohms.
How much resistance should a 3 phase motor have?
The reading should be between 0.3 to 2 ohms. If it is 0, there is a short. If it is over 2 ohms or infinite, there is an open. You can also dry the connector and retest to possibly get more accurate results.
How do I know if my 3 phase motor is bad?
Using a multimeter, check the continuity of motor winding from phase to phase ( U to V, V to W , W to U ). Each phase to phase must have a continuity if winding is OK. If any particular phase fails the continuity test, your motor is probably burnt.
What is a bad reading on a Megger?
What is a bad Megger reading? If the megger reads a resistance under 1 (1,000 ohms) on your meter after the initial 60-second interval, the cable has failed and the cable should be removed. If the megger reads a resistance between 1-1.25 on your meter, then the cable passes.
What is considered a bad Megger reading?
Turn on and read the meter. Anything reading between 2 megohms and 1000 megohms is usually considered a good reading, unless other problems have been noted. Anything less than 2 megohms indicates an insulation problem.
What is a bad insulation resistance reading?
The purpose of the IR test is to check for damaged insulation, this can be mechanical damage or damage by heat, (overloaded cables), readings less than 2 Mohm indicate damaged insulation, readings of 2-50 Mohm are indicative of long circuit lengths, moisture and contamination and do not indicate the insulation quality, …
What should be the insulation resistance of motor?
It is recommended that the insulation resistance of the motor should at least be 1 MΩ1）, and for the voltage to ground of 200 V, I0r should be 200 μA or below.
What causes motor windings to fail?
Looseness and bearing failures. … Another common fault stems from mechanical rubs, which can be the result of looseness of the motor shaft and/or the motor bearings. The most common mechanical faults are shaft imbalance, looseness, misalignment, and bearings.