# Why do you Megger a motor?

Contents

Megger testing measures resistance between the phase windings of the motor under test and ground. If there is an insulation breakdown, the resistance is negatively impacted and there is a departure between phases or between one measurement and a previous one and a determination of motor health is made.

## Why do we Megger a motor?

To measure the resistance in a three-phase motor, you will need a megohmmeter, otherwise known as a megger. Unlike an ohmmeter, a megger can measure high-voltage resistance values, which are generally the kinds of values you will encounter with three-phase motors.

## Why do we need to check the insulation resistance of a motor?

To prolong the life of electrical systems and motors, regular insulation resistance testing is required. Over the years, after many cycles of operation, electric motors are exposed to environmental factors such as dirt, grease, temperature, stress, and vibration.

## What does Megging a motor tell you?

It specifically tests the motor windings insulation. Depending on the insulation class of the motor, a good motor could measure well into Tera Ohms or 1,000,000,000,000 ohms! This is an insulation test of motor windings, commonly referred to as megging, to megger, or to meg a motor.

## What voltage should you Megger a motor?

The rule may be stated: Insulation resistance should be approximately one megohm for each 1,000 volts of operating voltage, with a minimum value of one megohm. For example, a motor rated at 2,400 volts should have a minimum insulation resistance of 2.4 megohms.

IT IS INTERESTING:  What is role of split ring in an electric motor?

## Can a Megger damage a motor?

Never use a megger if the motor windings are under a vacuum. … A high voltage for too long of a time may further weaken or fail motor windings and the winding insulation could be damaged by the testing procedure.

## What is a good motor Megger reading?

This is how the test works: DC voltage of 500 or 1000 V is applied between the windings and the ground of the motor.

A general rule-of-thumb is 10 Megohm or more.

Insulation resistance value Insulation level
5-10 Megohm Abnormal
10-50 Megohm Good
50-100 Megohm Very good
100 Megohm or more Excellent